NABL ACCREDIATED TRANSFORMER OIL TESTING LAB
We have NABL Approved Transformer oil test laboratory and render our service on short calls as and when required by you with our expert comments and suggestion promptly.
1. APPEARANCE TEST
|To Know about the Colour of the Sample and free from Sediments from its Appearance|
|This instrument used for the determination of acidic
constituents in transformer oil. This acid number is
used as a guide in the quality of transformer oil.
|The voltage at which the transformer oil breaks
down when subjected of AC electric field with
a Continuous voltage raise.
|This instrument used for measuring, under non-equilibrium condition, the Interfacial tension of mineral oil against water, which has been shown by practice to give reliable indication of the presence of hydrophilic compounds in transformer oil.
|This instrument used for measuring the Flash Point by Pensky Martens closed cup tester of transformer oil, fuel oils, lubricating oils, Suspension of solids, liquids that tend to form a surface film under test conditions and other liquids.|
|This Instrument used for the determination of water content in transformer oil unused or used insulating liquids with coulometrically generated Karl Fischer regent. We can measure from 1 ppm to 1000 ppm|
|This testing instrument to measure three important parameter in transformer oil - Tan Delta, Dielectric Constant and Resistivity of an insulating medium. Tan delta and Dielectric Constant balance with the aid of a synchronous and phase sensitive null detector. Resistivity with DC Voltage..|
|DGA is the most sensitive and reliable loss prevention
technique and it gives an early indication of abnormal
behaviour of transformer. This instrument measure the
concentrations of dissolved gas or free gases in
transformer oil and be interpreted to diagnose the
condition of transformer oil filled electrical equipment
in service and suggest future action.
|This instrument used for extracting dissolved gas from transformer oil..|
|Density is significant in determining the quality of an transformer oil and may be useful for type identification or to suggest marked compositional changes.|
|Used to determine the contamination muds,dust particles mixed in the Transformer Oil|
This method describes a producer for the determination of the kinematic viscosity of liquid petroleum products, both transparentand opaque, by measuring the time for a volume of liquid to flow under gravity through a calibrated glass capillary viscometer.
|This test method describes a standard procedure for determining the average viscometric degree of polymerization of new or aged electrical papers. The determination is made by measuring the intrinsic viscosity of a solution of the paper in an appropriate
|This Test method is to determine the degradation of cellulose paper insulation
High Concentration or unusual increase in the concentrations of furanic compounds in oil may indicate cellulose degradation from aging or incipient fault conditions
The levels of furanic Compounds in oil relate to the average deterioration of the insulating paper
This Instrument used for the analysis of 2- Furfural related furan compounds resulting from the degradation of cellulosic insulation and found in mineral insulating oil samples taken from electrical equipment.